Is the cable current? How many wires? If only three then you cannot genuinely use the 4 wire outlet correctly. Thank you for the support. I cannot truly make out the scematic that is attached above. Can somebody just inform me had been to hook up the 3 wires? I already took off the old 4 wire cord. I had a red, yellow and black wire and then a green wire that bent back near the bracket. I just wanted to be positive if I hook up only the three wires that it will not cause a fire or something. Please let me know what you consider. Thanks once again for all of your time and assistance.
For this use, three-wire circuits are permitted from subpanels as extended as SE cable (bare neutral) is not employed, and the grounded conductor is #10 or bigger Cu, or #8 or larger Al. For subs, three-wire has to have an insulated neutral. That seems to make sense, so you actually cant convert a three to four wire legally due to the fact there is no neutral and ground going back to the panel, unless you run a new four wire circuit.
Connect and tighten the new power cord wires on the terminal block correctly and according to the manufacturer’s recommendations. There will be some kind of connector holding the dryer cable to the wall of the dryer so that it does not pull out. The most frequent type is a clamp with two screws on the outdoors that can be tightened to squeeze the wire into spot. Loosen these screws so that the wire can slide out of the dryer.
FOR Security: Go to the dryer manufacturer’s web page and obtain the wiring diagram on how to attach the cord appropriately. The replacement cord you bought may well also have a How To Wire” diagram on it also. The dryer may perhaps also say on the back what colour and where the wires connect. Details contained inside is researched and backed by experienced DIY technicians. To transform the power cord your self, initial watch this video to get an notion of what is involved. Normally disconnect energy when undertaking any form of repairs on an appliance!
The very good news is that dryer cords are readily obtainable and relatively low-cost, and it isn’t incredibly hard to switch them. A screwdriver and a pair of pliers will do the job, despite the fact that some nut drivers would be nice. We aim to always provide relevant and engaging content exactly where details and data supplied is checked and rechecked for accuracy. Get behind the dryer and remove the terminal block access panel (modest panel with generally one particular screw securing it).
Thank you for the reply. On your dryer the yellow and white will connect with each other. Then the reds connect collectively. Last, connect the blacks. I have posted am image that should really be closer to you model. Please let me know if you have troubles. So a 3 wire coming from a major panel cannot be connected to a 4 wire dryer outlet. Any way you look at it the neutral and ground would have to be tied together either at the outlet or the at the dryer. None of this appears legal unless you run a new 4 wire from the panel.